Pryco Day Tanks
Pryco’s STANDARD Day Tanks are available in either a U/L Listed (Label #142) or a basic (non-U/L Listed) design. In addition to the standard features listed below, U/L Listed tanks have additional internal reinforcement, an emergency vent properly sized to the tank, and a U/L Listed label (File #MH12807 - Aboveground Tank for Flammable Liquids).
Standard features include:
- Removable 61⁄2" Square Inspection Plate
- Fuel Level Gauge
- Heavy Duty Float Switch
- Press-to-Test” Switch
- Pump Running" Indicator Light
- Four - 1" NPT Threaded Pipe Connections
- One - 2" NPT Threaded Pipe Connection
for Tank Vent
- Tank Drain (Sized To Tank Capacity)
- 1/3 hp thermally protected, 120vac, 1ph,
- 2 gpm bronze gear pump w/stainless steel
- Lift Lugs (on tanks 50 gallons and over)
- Removable top cover
- Epoxy coating inside
- Pryco (medium) Gray exterior paint (or an
industrial color of choice)
Pryco Tanks are fabricated of heavy gauge steel by certified welders. Each tank complies with NFPA 30 and is tested to 5 psi. Shown to the right is a 25-gallon, U/L Listed, single-wall Standard Day Tank (PY25UL) with an optional #465 U/L Listed Enclosed Industrial Control Panel.
Double Wall Tanks
A totally enclosed outer shell may be added resulting in a double wall construction. Both the inner and the outer tanks are vented separately and are pressure tested at 5 psi.
When enclosing a U/L Listed day tank, an additional emergency vent is added to the outer tank the same size as the inner tank. (The U/L Listing is “Secondary Containment Aboveground Tank for Flammable Liquids”, File MH12807.)
Day Tanks with a capacity of 25 gallons and more have all threaded connections located on the tank top (except the overflow, drains, and the double wall vent). The inner tank drain is piped through the outer shell.
All Day Tanks can be set in a Rupture Basin (open top dike), including a tank with double wall construction. See Option 385 for sizes.
A Double Wall or a Rupture Basin may be equipped with an optional Leak Detector that will shut down the pump motor, turn on an alarm light and provide contacts for a remote signal — Options 295 and 395.
Weatherproof versions are also available.
|SINGLE WALL||U/L LISTED SINGLE WALL||R/B|
|Size In US Gal.||Model||Weight||Model||Weight||Vent||Weight|
|DOUBLE WALL||U/L LISTED DOUBLE WALL||R/B|
"Far, far exceeded my expectations for what could have been a messy and smelly job."
"All at Comm Tank made a very stressful situation for us more than manageable. The men who came to do the work were always on time, extremely polite, and hardworking."
"In 34 minutes they achieved the removal without doing any cutting inside my home! Seeing is believing, which is why I sent you, today, the photos taken of their remarkable effort."
"Recently we hired your company Comm Tank to remove an underground oil storage tank buried in our front yard for many years. We also asked you to install a new aboveground oil storage tank next to our house."
William J. Lewis.
"They left the area cleaner than they found it. They were very friendly and fully explained how the tank was to be cut and removed."
"I would recommend Commtank to anyone who needs an oil tank removed. The price for such great service was very reasonable. Truly a good experience for me and my family."
"In the 40 years that I have lived in my house I have never had anyone do so much work, rip up so much sod yet leave everything in such a clean, neat and apparently undisturbed state."
"When I called for an estimate, Margie was very informative and one of the reasons I chose CommTank to do the work."
Jack E. Meyer, M.D..
"Paul’s recommendation along with the comfort level I felt dealing with your team made my decision to choose CommTank and easy one. Should I ever hear of anyone in need of a new oil tank I would recommend CommTank without hesitation."
"I also commend Luis Diaz on his pleasant, informative phone manner when we first spoke and at the time of the site exploration. His handing of the situation convinced me to go with CommTank."
Newton Centre, Ma
"I do mean all of them…you could be proud of them and know that they represent your company in a very professional manner. In today’s world, you very rarely see this."
Billl and Barbara Clough.
"Great job, completed on time, very aware of the Safety of our tenants."
Deborah M. McClory.
"CommTank just finished the UST removal job and the customer is absolutely delighted."
"I am emailing you with this word of “Thanks” to Comm Tank for one of the most professional companies I have used in quite sometime."
"I will recommend your company to my colleagues and clients."
"I had an oil tank removed yesterday, and the whole operation could not have gone more smoothly."
"What could have been a stressful situation actually went smoothly without any issues or surprises. I would recommend CommTank in a heart beat to anyone in need of their services."
Scott E. Lechter.
"There were many steps throughout the process and at every step I was very well informed. The scheduling, coordination and communication was simply outstanding."
"I want to thank you for your work in the oil tank removal at my mother’s house in Walpole."
"They left the basement much cleaner than when they started the job."
"Thanks for your help and the customer service that CommTank provided."
North Reading, Ma
"Your employees did a nice job and were a credit to your company in their professional work and attitude."
"Thank you for doing a very nice job!"
Prides Crossing, MA
"Your crew just left my site and they are wonderful, clean, great, and nice!"
"I would certainly recommend your company."
"These two excellent employees came early, at 7:15 a.m. Which is very appreciated by us, clients that have to leave for our jobs."
"They patched the holes left from removing the fill and vent lines like pros - I did not expect this level of service."
"Kim and I are very happy to have found you!"
"We want to tank your for a job well done while removing the underground oil tank."
"I wanted to thank you for a great job on the installation of the new fuel dispenser."
"Thank you for your donation of 200+ gallons of fuel through your CommTank Cares Program to St. Clement Parish Schools. Your generosity is certainly a help to our schools and parish."
Reverend Paulo Cumin.
"just want to express my appreciation for the excellent service that was provide to me in the removing of our 1,000 gallon underground oil tank."
"What I think I’ll never forget was how clean the basement was after the two men had removed the contaminated soil from our house. It had never looked like that!"
"Early this month your company removed my almost 40-year-old tank from my basement and installed a Roth Tank. I was extremely pleased with the results and with the crew that did the work."
"It was neat and clean and they left the area spotless. The gentleman who came back to inspect the job was kind and courteous."
"The City is extremely grateful to CommTank for its assistance in this cleanup. We believe we made a very wise choice in the selection of CommTank. Please feel free to use me as a reference for your team's pursuit of other environmental work."
Thomas G. Ambrosino.
"She called to brag about how professional the service was, and how clean and precise the installation was."
"We really appreciate the responsiveness to what was a worrying situation and the two men who performed the work were true professionals."
"This company is the best. The price was very reasonable, better than anyone else I contacted, about $300.00 less,"
"I had my oil tank and boiler removed from my home. Comm Tank showed up on time and finished the job quickly and neatly."
"I want to thank CommTank for the wonderful job that your crew did yesterday while removing and installing my oil tank."
"Thanks so much for getting your guys out here so quickly to take care of the issue. While they could not tell exactly what caused the seepage, they ended up replacing the red connector with the fill gauge to be safe."
"There were two crews on separate days that did a great job and were very knowledgeable about their job and company."
"As for me the customer, I am very pleased on the workmanship that was performed, and I would recommend ComTank to anyone that needs a new tank."
"Your workers were out at my house in Wayland last week and did a fantastic job removing the oil tank from my basement."
"The quality of their craftsmanship is buzzworthy, the work surpassed my expectations."
"They showed up on time, were extraordinarily efficient and neat, provided a comprehensive removal, and were very courteous in all our dealings."
John P Senko.
"You and your entire on-site crew, including Santiago and Carlos, all have been first-rate and first-class."
"Thank you for your competence and professionalism, your cheerful and hard-working staff, your expertise with regulations/compliance issues, and for referring us to Tommasino & Tommasino in Boston."
Richard and Kristen Henshaw.
"Please note that this appreciation comes from a person managing construction for clients for some forty years."
"Excellent work so far. We wish these guys were on all three Boston projects."
Peachtree Corners, GA
"He will refer us to anyone and will definitely be using our services again."
"Please let the crew know that I really appreciate the hard work and professionalism."
"I spoke to Cindy the other day and reiterated to her about how happy we were with our experience."
"The thorough explanation of what was to be done was excellent."
"During this past summer I had an underground oil tank removed and replaced with an indoor Roth oil tank, and was exceptionally pleased with the service."
"In my opinion they were very professional and courteous."
Mary Louise Thrower.
"Thanks again to you and your team for the high level of workmanship and customer performance you provided."
"Your company has been most professional, timely, and informative!"
"This was our first experience with your company and we were very pleased from start to finish."
"Your crew were great to work with and did a great job, although very hot out there, they continued on with no complaints."
"All of our clients are more than satisfied with the quality of CommTanks installations and LEO is as well."
"It was a pleasure having them work at my house."
"They quickly went to work and solved the problem. As worried as I was, Luis made me feel that everything was going to be ok. Luis was always there no matter how many times I called."
Jeffery J. Graham.
New Bedford, MA
"We were so pleased with the removal of the old furnace."
"They tore down part of a wall, shoveled, removed my old tank and replaced it with a new tank, also gave me some oil."
"They were courteous and professional, timely and completed everything as well as anyone could have asked."
"I have dealt with contractors before and was very impressed with your crew."